As a result of some specific engine adjusters, it may be necessary to carry out several starters in a relatively short time, preventing the engine from cooling down properly. It is important to remember that it is always important to emphasize that very long starts should be avoided, which may occur in cases where the motor torque is slightly higher than the torque converter, the overcurrent current absorbed while the rated speed is not reached can raise the risk the engine. Likewise, countercurrent braking, that is, by reversing the motor, can represent the cost equivalent to three starts.
Even considering external factors, it must be ensured that the starter torque is sufficient, either by choosing a suitable motor, or by verifying further that the power line has characteristics necessary to limit the voltage drop at the start; https://www.mrosupply.com/bearings/mounted-bearings/pillow-blocks/12963_ucpx08-24_ami-bearings/ or by keeping the load coupled to the motor under proper operating conditions so that it does not exhibit an abnormal resistant torque. In the case of an industrial process requiring frequent starts, this characteristic must be foreseen in the design of the equipment, and the motor must be adapted to work in this way.